How do you load a firmware update with the serial interface module ET 200S 1SI?
How to load a firmware update into the serial interface module ET 200S 1SI is described in detail in section 2.9.2 "Loading firmware updates" in the manual of the module concerned (Entry ID: 9260793). How to update the firmware of modules in general is described in detail in the STEP 7 Online Help under the topic of "Firmware Update".
The following requirements must be met:
|1||The ET 200S 1SI must be reachable online from the PG/PC.|
|2||The SI module must
be slotted in a station with a header module IM151-1 standard (6ES7
151-1AA04-0AB0) or IM151-1 HF (6ES7 151-1BA01-0AB0).
|3||The files with the new vision of the firmware must be available in the file system of your PG/PC.|
|4||STEP 7 V5.1 SP3 or new|
If when using the menu command "PLC > Update Firmware", the current firmware version of the module is not recognized or displayed, then the requirements for an update are not fulfilled.
PtP, Technology modules