MICROMASTER 4 (MM4): Routing between PG/PC and MICROMASTER 4 with ISO-Industrial Ethernet
Routing between PG/PC and MICROMASTER does not work although the PG/PC interface is set to ISO-Industrial Ethernet. What can I do?
To allow communication with Routing change the PG/PC Interface to "TCP/IP".
Open NetPro in your project.
Attached you find the procedure how to do it.
Ensure that your MICROMASTER and your PG/PC is connected-up as shown in the diagram
Next, your PG/PC must be assigned as shown in the next three screen shots.
Note: Please ensure that the checkmark for "Active" is set.
Right mouse click on PG/PC an choose assign PG/PC.
Choose your TCP/IP interface in tab assignment.
Checkmark S7ONLINE Access and confirm with Ok.
Now, the ROUTING should be active (this is shown by the yellow line).
- You have a technical question / problem: Ask the Technical Support
- You want to discuss in our forum and exchange experiences with other users
- You want to create CAx data for one or more products
- You would like to send us feedback on this Entry