Connecting external periphery to PCS 7 via IE/PB Link PN IO
Purpose of this document
The application shows how, in an existing system, field devices at a profibus from an external manufacturer can be parameterized via PCS 7 with the Process Device Manager (PDM).
The steps for the configuration of the IE/PB Link PN IO on a PCS 7 Engineering Station (ES) are described by in the example of the connection with a PROFIBUS PA device at a SIEMENS DP/PA Link.
This entry was created with SIMATIC PCS 7 V6.1 SP1 and V7.1, the procedure is transferable to higher versionen PCS 7.
09/2008 First release
05/2009 Revision IE/PB Link PN IO incl. PCS 7 V7.1