Entry type: Product note Entry ID: 4124456, Entry date: 08/27/1996
COM ET 200 V2.0 - Product Information
Concerns products with the Catalog Nos.: 6ES5 895-6SE12 COM ET 200 Windows with manual, German 6ES5 095-8ME01 S5-95U mini PLC, L2-DP master 6ES5 998-3ES12 ET 200 manual, German If the COM ET 200 Windows V2.0 is installed on a PG 740/760 Pentium with Windows '95 operating system and the usual default settings, no download function to an S5-95U DP master will be possible. In the case of PG 740/760 Pentium programming devices the address area for the MPI interface within the CONFIG.SYS is not excluded and IRQ=5 is set. If you want to use the MPI inter- face for downloading, please alter the settings as follows: - Open the file L2PC_ _DRV.INI in the directory ÖCOMWIN20Ö KERNELÖ - Search for the parameter IrqNr=.. in the parameter block ÄMPI_ _1Ü. The MPI card accepts the interrupts 10, 11, 12 and 15 in conjunction with the COM ET 200; from this group, enter a free interrupt of your PC system. To determine a free inter- rupt, help can be sought in the Hints for the DP Card in the program group COM ET 200. - Search for the parameter PhyAdr=.. within the parameter block ÄMPI_ _1Ü and set the address of the MPI card there. To determine the real address, seek help once again in the Hints for the DP Card in the program group COM ET 200. Close the file. - Open the file CONFIG.SYS in the root directory. - Search for the entry DEVICE = C:ÖDOSÖEMM386.exe noems X=... I=... Exclude the memory area that your MPI card occupies. Example: Your card is located in the area 0xC800; exlude this area by carrying out the following extensions: DEVICE = C:ÖDOSÖEMM386.exe noems X=... X=C800-C8FF. Take care that this area is not included in the same line by i=... - Close the file and carry out a restart, so that the changes become effective. With version 2.1 of the COM ET 200 Windows (see User Info 96/14 /012), these settings are carried out by the installation rou- tine of the COM. -------------------------------
In order to protect technical infrastructures, systems, machines and networks against cyber threats, it is necessary to implement – and continuously maintain – a holistic, state-of-the-art IT security concept. Siemens’ products and solutions constitute one element of such a concept. For more information about cyber security, please visithttps://www.siemens.com/cybersecurity#Ouraspiration.
Feedback for the article with the entry ID 4124456
Personalization saves you typing! If you have already been registered, you can login directly. If you are not registered yet, you can inform and register yourself without obligation here (our service is free of charge).
Number of characters: 0 (max. 500)
Send copy of comment to sender. (login required)
Note: The feedback always relates to the current entry / product. Your message will be forwarded to our technical editors working in the Online Support. In a few days, you will receive a response if your feedback requires one. If we have no further questions, you will not hear from us.
Requests and feedback
What do you want to do?
- You have a technical question / problem: Ask the Technical Support
- You want to discuss in our forum and exchange experiences with other users
- You want to create CAx data for one or more products
- You would like to send us feedback on this Entry