How do you load a project into the CPU in STEP 7 (TIA Portal)?
To load project data into the CPU you need an online connection between your programming device and the device or CPU. Under circumstances it might be necessary first to reset the S7-1500 CPU to the factory settings if the module memory is not initialized automatically. If the CPU has only one IP address and no hardware configuration has been downloaded, you will always get the "Not compatible" message during the online connection.
In the project navigation, you mark the folder (PLC_1, for example) whose project data you want to load into the CPU and then you execute the menu command "Online > Download to device" or click on the "Download to device" icon in the toolbar. The changed project data (device configuration and the STEP 7 program) are then loaded into the CPU.
Alternatively, you can load separate components like the hardware configuration and the software blocks. If you right-click the "PLC_1" folder in the project navigation, the following menu commands are offered in the pop-up menu:
With the first download the "Extended download to device" dialog opens. Here you have to define your PG/PC interface. In the drop-down list boxes you select your configuration data and then click the "Start search" button.
The IP address of your CPU configured in the device configuration must match the IP address of the CPU that is accessible online.
|3||After the node has been found, the station is displayed with the IP address in the "Compatible devices in target subnet" table. In the "Online status information" field you also get the confirmation that the online connection to the device has been established with the expected IP address. Click the "Load" button.|
The Ethernet interface of your programming device must be in the same IP band as the module to be configured. If an IP address has already been assigned for your PG/PC, you no longer get the dialog shown in Fig. 4. Click the "Yes" button.
Also confirm the next message.
The project data must be consistent. If the project has not been compiled, the project data is compiled automatically before being loaded. In the "Load preview" dialog, messages are displayed and the actions required for loading are proposed.
Click the "Load" button.
Finally, the "Results of the download procedure" dialog opens informing you whether the loading procedure was successful. Click the "Finish" button to put the CPU into "RUN" mode.
In the inspector window, go to "General > Info" for detailed information about the load procedure.
|7||After you have loaded the project data into the CPU and put the CPU back into "RUN" mode, you can execute the test and diagnostics functions on your CPU.|
Note on downloading an earlier version of STEP 7 TIA Portal (S7-1200 CPU)
If you have loaded a project with STEP 7 TIA Portal V12 (or higher) into an S7-1200 CPU and would then like to make more downloads with an earlier version of STEP 7 (V11, for example), you have to reset the CPU to the factory settings. You can do this either with the current version of STEP 7 TIA Portal or with a Micro Memory Card.
Note on S7 routing to an HMI device (S7-1500)
The S7 routing to an HMI device cannot be executed if the option "Use different method to assign IP address" is enabled in the Properties of the CPU S7-1500 (Fig. 3). Connect the HMI device over the second PROFINET interface [X2], because a fixed IP address point is needed from the STEP 7 project for S7 routing.
More information is also available in the STEP 7 TIA Portal Online Help under "Download into CPU".
The screens in this FAQ response were created with STEP 7 (TIA Portal) V13.
- You have a technical question / problem: Ask the Technical Support
- You want to discuss in our forum and exchange experiences with other users
- You want to create CAx data for one or more products
- You would like to send us feedback on this Entry