Firmware update for ET 200SP DI 8X24VDC ST
When firmware is updated, it must always be updated to the latest version available for the relevant article number.
A detailed description of performing the firmware update is provided in the entry 78646133.
If an I/O module is replaced or upgraded by means of a firmware update, the firmware of the interface module may also need to be updated.
The following table shows the interface module versions for which an update is necessary:
|Article number||Minimum firmware version||Regards supply from|
Siemens stock until ca.
|IM155-6PN ST (PROFINET)||6ES7155-6Ax00-0BN0||V1.1.1||12/2013|
|IM155-6DP HF (PROFIBUS)||6ES7155-6Bx00-0CN0||V1.1.0||12/2013|
|IM155-6PN HF (PROFINET)||6ES7155-6AU00-0CN0||V2.1.0||12/2013|
Therefore, we urgently recommend that you update the firmware of the interface modules listed above for IMs with a firmware version lower than the minimum firmware version.
Overview of article numbers and current revision levels of the ET 200SP DI 8X24VDC ST:
Upgrade by means of...
For a description, see below Update V1.1.1
For STEP 7 version 5.5
For STEP 7 TIA Portal
Optimizing PROFIenergy behavior
A firmware update is only supported as of product version 03 of the module.