SM 336, f.AI 6 X 0/4 ... 20mA HART
SIMATIC S7, Analog input SM 336, 6 AI; 15 bit; fail-safe analog inputs for SIMATIC Safety, with HART support, up to Category 4 (EN 954-1)/ SIL3 (IEC61508)/PLE (ISO13849), 1x 20-pole
- Save filter
- Load filter
- email on update
Validity: Products of the Operating Company DI (Digital Industries) and Business Unit SI CP (Control Products) of Siemens AG.
When setting the IO addresses of a fail-safe ET 200M module it might happen that you get the following error message when quitting the configuration window: Object Properties (2988:2074): "The IO address: [IO initial addresses] must not exceed the maximum process image of the CPU. For the set process image and used module the maximum permissible address is [xxxx]."
You can use the CAx download manager to access the latest product data for your CAD or CAE system.
With ET 200S and ET 200M you can use fail-safe and standard modules combined. Additional measures have to be taken for some modules in this respect.
Contrary to binary signals, analog signals take any number of values within a specific range. You have to convert or standardize and destandardize the analog values before you can process, display or output them.
The number of ET 200M bus modules you can mount on an ET 200M mounting channel depends on the following:
The ABB system does not fully support the standard redundancy in accordance with "Specification Slave Redundancy V1.2, Nov. 2004 by the PROFIBUS User Organization; Order No: 2.212".
With enabled HART communication the F-AI is rendered passive and the diagnostics buffer displays error message 16#F580:0F01. You can prevent this by parameterizing the "HART gateway".
The following instructions show you how to find the UL certificate on our Support pages taking the example of an S7-1500 digital input module (article number: 6ES7 521-1BL00-0AB0).
Maintenance request when allocating NameOfStation. The MAINT LED of the CPU lights up yellow.
SIMATIC modules of the product families S7-300 S7-400 ET 200M ET 200S ET 200iSP TDC are also approved for implementation in environments with high concentrations of corrosive gas in compliance with ISA–S71.04 severity level G1; G2; G3. ...
Description There are various fail-safe modules of the distributed I/O available depending on the fail-safe controller used. ...
Description When implementing a software redundancy configuration with two IM 6ES7153-2BA..-.... (hereinafter call IM), it might happen that when both IMs are switched on at the same time not all the modules (SM3xx, FM3xx, CP3xx, etc., hereinafter called IO) are not parameterized when the IMs are started up. ...
Description In the case of underflow of the 4 mA limit, a negative value is output (e.g. -1 is output for 3.9995mA), which becomes steadily smaller until at 1.185 mA the value -4864 (decimal) or ED00 (hexadecimal) is reached. ...
Description: The tables below list the documentation concerning the Distributed I/O Device ET 200M. ...
QUESTION: Why can I not set a partial process image for my I/O module? ANSWER:...