MICROMASTER 420 UNFILTERED 1/3AC 200-240V +10/-10% 47-63HZ CONSTANT TORQUE POWER 1.1 KW OVERLOAD 150% FOR 60S VARIABLE TORQUE POWER 1.1 KW 202 X 149 X 172 (H X W X D) PROTECTION IP20 AMBIENT TEMP -10 TO +50 DEG C W/O AOP/BOP
- Save filter
- Load filter
- email on update
01/2018, Getting Started, A5E02779537A-AF
Irrespective of the particular application, whether you require online help for a specific machine message when operating a product, you wish to take the time and get to know a product or you wish to compile documentation for your own individual purposes: With us, you can find the current editions of technical documentation electronically, on data carrier and printed out.
Discontinuation of the KTY84-130 temperature sensor / Impact on SIMOTICS motors for Motion Control, motor spindles (Fa. Weiss) SINAMICS, SINUMERIK, SIMOTION
Unfiltered (industrial) variable speed drive must be able to be installed in a power drive system in compliance with category C3 EMC requirements for CE certification.
My PG/PC has only USB ports. How can I go online to my inverter using USS protocol?
Test Certificates, Declaration of the Compliance with the order 2.1, Manufacturer, Ex t, converter operation (Micromaster, ET200S-FC, Simovert Masterdrives VC, SINAMICS G110) A5E38572797A
Test Certificates, Declaration of the Compliance with the order 2.1, Manufacturer, Ex n, converter operation (Micromaster, ET200S-FC, Simovert Masterdrives VC, SINAMICS G110) A5E38402476A
Statement to China-RoHS directive for Low-voltage products
The 2-wire method allows the inverter to be started and stopped by using only 1 digital input in combination with the internal 24 V supply of the inverter. For most applications the 2-wire method is adequate to start and stop the inverter. The 3-wire control allows the inverter to be started and stopped directly with a press of a switch. This method is setup by using BiCo technology.
p0350 Stator resistance value in [Ohms] for connected motor (from line-to-line).
“Speed accuracy” is the ability of an inverter to maintain the speed corresponding to the speed setpoint when the load is kept constant
This FAQ applies only to the SIMOVERT P (6SE20/21), MICROMASTER, SINAMICS G120 (CU2x0x) inverters. Description.
In this FAQ we used Starter Version STARTER V22.214.171.124.
This FAQ applies to MICROMASTER 4 and SINAMICS G120.
MICROMASTER 4 drive inverters can be parameterized using the DriveMonitor and STARTER commissioning tools.
Applies to MICROMASTER 4
EPLAN Electric P8 is a CAE system for the electrical configuring of electric equipment (e.g. control cabinets). It supports the designer in the configuring, documentation and management of projects.
In many applications, when fieldbus (PROFIBUS, PROFINET) communication fails with fault F0070, it is desired to have a bit that signals that fieldbus has failed, and that can then also be freely interconnected. This means that the user can specifically evaluate this fault and himself decide which response is to be made.
When Starter is connected to an inverter and parameter changes are made, the changes are either saved in the inverter RAM or ROM memory depending on the Starter settings.
The technical documentation for the four product families is provided online in the Siemens Industry Online Support.