- Save filter
- Load filter
- email on update
The IOP (Intelligent Operator Panel) has been available for delivery since 2009. Since this time the operator panel has been supplied with different software versions.
This entry provides information on side-by-side mounting.
This entry contains information on compliance with the limits for electromagnetic emitted interference.
The Virtual Controller (VC) makes it possible to run automation programs in MS Windows. However, you should note that there are a number of differences between the VC and a real CPU.
To close WinCC you should always use the appropriate buttons and functions to avoid damage.
VBScript is supported by the WinCC (TIA Portal) edition WinCC Comfort onwards. The manuals and information system of WinCC (TIA Portal) provide diverse information about programming Visual Basic Scripts.
Line voltage compensation is only available with the SIPLUS HCS4200 if a PM4000 U/I is connected.
Depending on the system conditions, there might be high starting currents when you switch on the SIPLUS HCS4x00, which might damage certain upstream contactors.
The SIPLUS HCS4000 IO module U/I provides the following functions:
The IO module PM4000 Temperature is slotted in the Central Interface Module (CIM) of the SIPLUS HCS heating control system and has 4 analog inputs for 0...20 mA and 4 measuring inputs for temperature.
If you observe the following effects, you can also operate the Power Output Modules of the SIPLUS HCS4200 as single-phase.
If you stack the subracks of the SIPLUS HCS4200 one on top of the other, you have to have the fan in the top row switched on permanently via the data record 160.
With the SIPLUS HCS4x00 heating control system an error is signaled in the Online mode of the TIA Portal via the message "Error" in the diagnostic status of the module.
Microsoft regularly rectifies security gaps in its products and makes these fixes available to users via product updates.
If the Kaspersky virus scanner is installed on a computer, then installing the HSP SINAMICS firmware V4.7.9 in Startdrive V14 SP1 might lead to problems under certain circumstances.
When scrolling through alarm logs in an alarm display, the window content suddenly shifts if a new alarm arrives while viewing. This FAQ response describes how to retain the scroll position in the view despite arrival of new alarms.
Reading out an Audit Trail file via a Comfort Panel and WinCC Runtime Advanced.
Driver blocks for analog modules of the "PCS 7 Advanced Process Library" use unit inputs that have to be parameterized with an integer value. This integer value of the units of measure is defined by "Profibus and Profinet International" and is documented in the specification "PA Profile for Process Device".